In many of the places we work, solar pumping is more economical than other power sources. It is particularly good when grid power is unreliable, and where managing diesel generators is a headache. Advantages include:
- Solar pumping can be fully automated
- No managing fuel
- No need for batteries - store water in a tank instead
- Economical across much of the world
Solar power is the preferred choice and the first option that all Oxfam projects should consider for off grid pumping.
Oxfam Technical Brief 14: Solar powered borehole pumps
Get the Solar Toolkit
Planning & design
- Solar powered installations should be the first option for all off-grid water pumping projects.
- All solar installations should be properly designed, preferably using dedicated software.
- Systems should be sized to ensure there is enough water available during the worst time of year.
- Provision should be made for days when there is very low solar irradiation - either through accepting lower reliability (if other water sources are available), installation of a backup or hybrid power source (generator or grid connection), or appropriately sized backup water storage.
- Given the flow rate of water from solar powered pumping changes throughout the day, special consideration should be given to how chlorination or other water treatment will be undertaken. For example, a variable flow chlorine doser may be necessary.
- Where possible the system should be fully automated. This will increase system reliability.
- Always remember that even a single solar module is a
live circuit that can result in electrocution. Fix all modules securely onto the support structure
before doing any wiring and minimise the risk of
accidents by covering and shading modules with their
packaging until the installation is complete.
- All DC wiring should, if possible, be completed prior to
installing a PV array. This will allow effective electrical
isolation of the DC system while the array is installed;
and effective electrical isolation of the PV array while
the inverter is installed.
- Solar modules consists of glass which can easily
break. Do not throw objects at the solar module, stand
or step on the module or try to repair your solar
module if it breaks.
- Two or more modules connected in parallel or series
if connected incorrectly to a pump can damage or
destroy the equipment. Do not carry out modifications on your system without technical guidance from your system supplier or a
- Modules that have different characteristics in model,
power, voltage and current should not be connected
together in the same system (mismatching)
- Shadowing should be avoided as it leads to significant